Use this display to control the outlets on supported APC Rack PDU devices.
You must specify the write community name for the Rack PDU device at device discovery,
or in the Device > SNMP Device Communication Settings > Device Scan Settings.
You can configure delay parameters for the outlets via SNMP or by logging into the device.
A Communication Error is displayed when the Rack PDU device does not respond to a
command for any reason, for example, when the write community name in the
Device Scan Settings is incorrect.
User permissions defined in System > Users and User Groups > Modify Device Group Access determine which users have access to outlet control. Data Center Expert Server Administrators, Device Administrators, and Device Viewer users with monitoring access set for Administration Access or View
and Control can access outlet control.
CAUTION: When you perform a command at an outlet that is part of an outlet group, that
command will be executed at all outlets in the group. The Data Center Expert server cannot
determine which outlets are part of an outlet group.
Please sign in to leave a comment.