In the Cooling Optimize web client you can edit the temperature set points used for cooling control and turn the cooling units on and off. Because of this, you need user rights to be able to launch to the Cooling Optimize web client. Go to System Setup > User Rights and Authentication > Launch to Cooling Optimize > Save and close.
To launch the web client go to the right-click menu of any Cooling Optimize item and select Launch to Cooling Optimize.
In the Set Points tab you can view and change the temperature set points of your racks.
The Equipment tab shows the state of the equipment, e.g.: cooling rate, power usage, and origin of on/off control. This is where you can manually override units in the facility and where you can turn your cooling units on and off.
For more information go to the help icon in the top right corner of the web client.